A Turgo turbine is a type of hydro turbine (specifically an impulse turbine), developed in the 1920s, that is a variant of the Pelton turbine. The main difference between a Pelton turbine and a Turgo turbine is that Turgo turbines use single cups instead of double cups on the wheel, and these cups are more shallow. The water in a Turgo turbine is moving quickly (high velocity head, figure 2) and the turbine extracts energy from the water by slowing the water down, which makes this an impulse turbine.
The Turgo turbine is an impulse turbine, and can handle flow rates that are higher than those a Pelton turbine can handle. This ability to deal better with large volumes of water gives the Turgo turbine an advantage when used in hydroelectric plants that have medium hydraulic heads. Although they are better able to deal with high flow rates, Turgo turbines are slightly less efficient.
Since the runners on these turbines are smaller and faster spinning, some Turgo turbines can be connected directly to a generator instead of having to use a speed-increasing transmission. This direct attachment is shown in Figure 1.
The design of a Turgo turbine is very similar to that of a Pelton turbine. Essentially, a Turgo turbine is a Pelton turbine cut in half. A large circular disk is mounted on some sort of rotating shaft known as a rotor. Mounted on this circular disk are cup shaped blades known as buckets evenly spaced around the entire wheel. Then nozzles are arranged the wheel and serve the purpose of introducing jets of water to the turbine. Jets of water emerge from these nozzles at some relatively shallow angle. This causes the turbine to spin as a result of the impact of the water jets on the buckets.
The operation of a Turgo turbine is very similar to that of a Pelton turbine. In this type of turbine, high speed jets of water emerge from the nozzles that surround the turbine. These nozzles are arranged so the water jet will hit the buckets on one side at an angle of around 20°. This shallow angle allows the water stream to exit on the other side instead of being diverted backwards. Since the incoming and outgoing jets don’t interfere like they do in Pelton turbines, this type of turbine is able to accommodate a higher flow rate.
Turgo Hydro Turbines
Turgo Impulse turbines are applicable for medium to high head applications and overlap the boundary of Pelton and Francis machines. These turbines are well suited to “run of river” schemes as they can tolerate some “dirty water” and perform well over a wide flow range. Whilst their peak efficiency is lower than Francis machines, they can often generate more energy due to their flat efficiency curve and high partial load efficiency, and as such can be preferable where considerable water supply fluctuations are experienced. The use of deflectors can mitigate issues of pressure surges in the upstream pipework, even on full load rejections.
FEATURES OF TAMAR TURGO TURBINES
- Compact design
- Available in single, twin or three jet configurations
- Robust design and manufacture
- Designed for minimal maintenance
- Fixed, manually variable or fully automated flow regulation
- Horizontal or vertical configuration
- Can be manufactured in a range of materials to suit the customer’s requirements
- Output to 10MW per machine